PRODUCTION: 1.5 TONS / DAY OF CLEAN, DRINKING WATER
OUT OF FRESH WATER – RIVER WATER, LAKE WATER OR CLEAN FRESH WATER
CONFIGURATION: COMMON SKID WITH ALL COMPONENTS PRE-ASSEMBLED
OPERATING ENVIRONMENT TEMPERATURE: UP TO 50 C
SCOPE OF SUPPLY:
A) Mounting Frame SS304 / Aluminium powder painted.
All components connected, tested & working.
B)Set of Filters:
-Inlet Filter for bigger particles 80 Micron Disc Filter Hand Backflush
-Second inlet filter for smaller particles 5 Micron – 10 inch long
-Carbon filter to improve the smell – after unit, 10 inch long
C) 2 Pcs RO Membranes 4021 for fresh water (max 15 bars).
Includes the Membrane Pressure Vessels.
*Membranes prepared for instalation outside the machine
D) Feed Pump – SS 316 – 3 m3/h 3 BAR
To increase pressure on inlet and bigger flow in inlet filter.
Remark: non self priming pump SS, Maker: Grundfos
E)Working pump – for fresh water, 4m3/h 6 BAR
For RO membranes operation 3 x 400V
Maker: Grundfos horizontal pump – low pressure 6 bars
F)Electric box – black steel, galvanised and powder painted
Pumps and all electrical components protected, control 24VDC.
Power Supply: 3 Phase, 400V / 50 Hz
Includes low pressure protection for pumps and electrical protection for el. motors.
With hand operated backflush filter.
G) 3 Pcs Rotameters for water flow and operation control
H) 2 Pcs Manometers for pressure and operation control
I) All necessary valves and pipings (all components atested for drinking water).
components with water contact – professional, made in SS 316 or 304 or Plastic PP
J) 1 Pc Electronic salinometer for operation control
K) Cleaning tank/ prevention tank – included with all valves
L) Dosing system (hand operated)
M)Pickling “Y” Valve
N)Pressure Regulation (Manual)
Inlet flow: 1 m3/h of dirty river water 500-5000 ppm.
Product (ultra clean demineralised water for drinking): 70 l/h (up to 1.6 tons/day).
product max 1% OF INCOMING SALT THAT IS 5 – 50PPM
Country of Origin: Poland